210.63 Heating, Air-Conditioning and Refrigeration Equipment Outlet Article 210 specifies provisions for all branch circuits except for branch circuits supplying only motor loads, which are covered in Article 430.
As commercial, industrial and educational facilities become more dependent on information technology (IT) equipment for performing the day-to-day tasks, the quality of electrical supply that powers these growing loads becomes more of a factor.
A presentation at the PQ World 2002 Conference in October re-enforced the need to continue to make the electrical workplace a safer place to work in. While it would be ideal, it’s not always possible to de-energize electrical systems before working on them.
* For reference figures, please refer to ELECTRICAL CONTRACTOR magazine. 210.52(D) Bathrooms Requirements pertaining to receptacle placement inside and outside dwellings are covered in 210.52(A) through (H).
SAN JOSE, Calif.† December 10, 2002† The compelling need to protect modern communication networks in data centers, base stations, and colocation sites from power disturbances is driving the demand for power quality (PQ) equipment and services in North America.
CODE CITATIONS Article 225 Feeders Article 230 Services Article 250 Grounding Article 408 Switchboards and Panelboards Article 445 Generators Article 680 Swimming Pools, Fountains and Similar Installation Systems NFPA 20 1999 Standard for the Installation of Stationary Pumps for Fire Protection Grou
* For referenced figures, please refer to ELECTRICAL CONTRACTOR magazine. If the data recorded appears to violate the laws of physics, apply the test of reasonableness to the data before attempting to fix something that isn't real.
CODE CITATIONS Article 100 Definitions Article 210 Branch Circuits Article 230 Services Article 250 Grounding Article 312 Cabinets, Cutout Boxes and Meter Socket Enclosures Article 445 Generators Article 518 Places of Assembly Disconnect for multiwire branch circuit Q: There was a requirement in the
A load or circuit with significant loads that have rectified inputs will most likely have a true power factor (W/VA) that is less than displacement power factor (cosine of angle between voltage and current).
210.52(C)(5) Receptacle Outlet Location Provisions stipulating the placement of receptacle outlets are covered in 210.52 through 210.63. Requirements for placing receptacles in dwelling units are located in 210.52(A) through (H).