Grounding-electrode continuity Q: Does the grounding-electrode conductor to driven ground rods have to be unbroken to both rods or may a splice be made at the first rod, then continue to the second ground rod by installing two ground clamps at the first ground rod, then continuing to the second rod
Flexible cord terminations Q: May a properly sized flexible cord with 15-ampere male attachment plugs on both ends be used to supply an optional standby generator for a small business? The cord is intended to plug into a receptacle on the generator and a receptacle on the outside of the building.
In the 2002 and previous editions of the National Electrical Code, the metal frame of a building or structure was required to be used as a grounding electrode when the metal of the building or structure was effectively grounded.
Ground-fault circuit interrupter (GFCI) protection for personnel or a similar protection technique has been in the National Electrical Code (NEC) since 1962 with specific reference to GFCI and its definition found in the 1968 NEC.
Article 210 Branch Circuits Article 240 Overcurrent Protection Article 250 Grounding Article 310 Conductors for General Wiring Article 430 Motors, Motor Circuits and Controllers Branch-circuit size for motor load Q: I have to install a 11/2 horsepower, single-phase, 120V motor with a nameplate full
Article 210 Branch Circuits Article 250 Grounding Article 310 Conductors for General Wiring Article 320 Armored Cable: Type AC Article 404 Switches Derating Cables Q: Is it necessary to derate types NM-B, AC or MC cables where these cables are bundled to enter a branch-circuit panelboard?
The basis of grounding and bonding starts at the connection of a bonding jumper or an equipment-grounding conductor to a box, an enclosure or other electrical equipment and ends at the point of connection to the service-grounded conductor in a grounded system or at the service-equipment enclosure fo
Article 110 Requirements for Electrical Installations Article 250 Grounding Article 310 Conductors for General Wiring Article 312 Cabinets, Cutout Boxes and Meter Socket Enclosures Article 430 Motors, Motor Circuits and Controllers Article 518 Places of Assembly Thermostat as motor disconnect Q:May