I made a comment while teaching a class that nonmetallic (NM) cable was not permitted in an outdoor, wet location. An attendee took exception to that statement and asked me to provide National Electrical Code (NEC) justification for the assertion.
Please enter your information below to subscribe to ELECTRICAL CONTRACTOR's monthly e-newsletter.
© 2003 - 2013. All Rights Reserved.Electrical Contractor: 3 Bethesda Metro Center, Suite 1100, Bethesda, MD. 20814-5372 | Phone: 301.657.3110 | Fax: 301.215.4501