At a recent National Electrical Code (NEC) update seminar,
I was asked about the new requirements to install a grounded (neutral) conductor in a box for switches that control lighting loads.
Please enter your information below to subscribe to ELECTRICAL CONTRACTOR's monthly e-newsletter.
© 2003 - 2016. All Rights Reserved.Electrical Contractor: 3 Bethesda Metro Center, Suite 1100, Bethesda, MD. 20814-5372 | Phone: 301.657.3110 | Fax: 301.215.4501