Article 110 Requirements for Electrical Installations Article 250 Grounding Article 310 Conductors for General Wiring Article 312 Cabinets, Cutout Boxes and Meter Socket Enclosures Article 430 Motors, Motor Circuits and Controllers Article 518 Places of Assembly Thermostat as motor disconnect Q:May
The basis of grounding and bonding starts at the connection of a bonding jumper or an equipment-grounding conductor to a box, an enclosure or other electrical equipment and ends at the point of connection to the service-grounded conductor in a grounded system or at the service-equipment enclosure fo
Article 314: Boxes, Conduit Bodies, Fittings and Manholes 314.16(A) Box Volume Calculations Article 314 of the National Electrical Code covers the installation and use of all boxes and conduit bodies used as outlet, device, junction or pull boxes depending on their use.
Article 210 Branch Circuits Article 250 Grounding Article 300 Wiring Methods Article 404 Switches Article 408 Switchboards and Panelboards Article 430 Motors, Motor Circuits and Controllers Article 527 Temporary Installations Also mentioned are the General Information for Electrical Equipment Direct
Brush up on what the NEC says about air conditioning During the hottest parts of the summer, most people do not notice the sound of air conditioning units turning on and off, but if a unit fails to start, the effect is noticed immediately. Comfort becomes a premium to be restored at all costs.
One of the most important NEC requirements (and yet one most often ignored) is 110.22: Identification of Disconnecting Means. It reads: “Each disconnecting means shall be legibly marked to indicate its purpose unless located and arranged so the purpose is evident.
Photovoltaic (PV) modules convert sunlight into electrical energy that can be used to provide power for specific loads within a building in a standalone system or as a supplement to the building’s utility power supply in an integrated system.
220.19 Electric Ranges and Other Cooking Appliances Specifications for calculating branch-circuit, feeder and service loads are in Article 220 of the National Electrical Code. This article is divided into four parts: I. General, II. Feeders and Services, III.
220.19 Electric Ranges and Other Cooking Appliances Branch-circuit, feeder and service-load calculation provisions are in Article 220 of the National Electrical Code. While Part I is titled “General,” most of the first part pertains to branch-circuit calculations.