With the acceptance of the 2005 National Electrical Code (NEC), installing and servicing fluorescent luminaires (fixtures) has become a complex situation. The design and layout of the lighting system is critical in determining certain required added features.
Grounding-electrode continuity Q: Does the grounding-electrode conductor to driven ground rods have to be unbroken to both rods or may a splice be made at the first rod, then continue to the second ground rod by installing two ground clamps at the first ground rod, then continuing to the second rod
314.16 Number of Conductors in Outlet, Device, and Junction Boxes, and Conduit Bodies The scope of Article 314 is covered in 314.1 and covers requirements pertaining to the installation and use of all boxes and conduit bodies used as outlet, device, junction or pull boxes, depending on their use, a
For approximately 40 years, unprotected or improperly protected penetrations have presented a subject of much concern to the fire-protection community. In 1996, an electrical fire occurred at 30 Rockefeller Plaza in New York City.
314.16 Number of Conductors in Outlet, Device, and Junction Boxes, and Conduit Bodies The National Electrical Code contains provisions that limit the numbers and sizes of conductors that can be installed in boxes and conduit bodies.
Flexible cord terminations Q: May a properly sized flexible cord with 15-ampere male attachment plugs on both ends be used to supply an optional standby generator for a small business? The cord is intended to plug into a receptacle on the generator and a receptacle on the outside of the building.
The installation of photovoltaic (PV) equipment is governed by a number of industry codes and standards. Electrical contractors need to be aware of the codes and standards to ensure a safe and functional PV installation.
The text in Section 230.40 covering the number of sets of service-entrance conductors for each service drop or lateral has not changed since it was accepted into the 1984 National Electrical Code (NEC).
According to the Design-Build Institute of America (DBIA) “Design-Build is a process that has been embraced by the world's great civilizations. In ancient Mesopotamia, the Code of Hammurabi (1,800 BC) fixed absolute accountability upon master builders for both design and construction.
314.16 Number of Conductors in Outlet, Device, and Junction Boxes, and Conduit Bodies The National Electrical Code has specific requirements detailing how to calculate the maximum number of conductors in boxes (outlet, device, junction, etc.) and conduit bodies.
314.16 Number of Conductors in Outlet, Device, and Junction Boxes and Conduit Bodies Section 314.1 covers the scope of Article 314. This article covers the installation and use of all boxes and conduit bodies used as outlet, device, junction or pull boxes, depending on their use.
Twenty-five years ago, the National Fire Protection Association (NFPA) first prepared a set of standards to ensure electrical workers were safe on their jobs. So why has this standard-known as the NFPA 70e-suddenly become such a big deal?