314.16 Number of Conductors in Outlet, Device, and Junction Boxes and Conduit Bodies Section 314.1 covers the scope of Article 314. This article covers the installation and use of all boxes and conduit bodies used as outlet, device, junction or pull boxes, depending on their use.
Twenty-five years ago, the National Fire Protection Association (NFPA) first prepared a set of standards to ensure electrical workers were safe on their jobs. So why has this standard-known as the NFPA 70e-suddenly become such a big deal?
In the 2002 and previous editions of the National Electrical Code, the metal frame of a building or structure was required to be used as a grounding electrode when the metal of the building or structure was effectively grounded.
Article 314 C Outlet, Device, Pull and Junction Boxes; Conduit Bodies; Fittings; and Manholes 314.16(B) Box-Fill Calculations Article 314 of the National Electrical Code contains requirements pertaining to the installation and use of all boxes and conduit bodies used as outlet, device, junction or
Ground-fault circuit interrupter (GFCI) protection for personnel or a similar protection technique has been in the National Electrical Code (NEC) since 1962 with specific reference to GFCI and its definition found in the 1968 NEC.
The required placement of receptacles in the wall above a kitchen countertop is uncertain where an appliance garage is present. The Code requirements are the following: “210.52 Dwelling Unit Receptacle Outlets. (C) Countertops (1) Wall Counter Spaces.
The electrical contractor's job on a typical construction project goes beyond the scope of traditional electrical installations. It's a two-part responsibility that includes the construction or renovation of electrical systems for the structure.