Disconnecting means Q: Disconnecting means for circuits supplied by a generator are required where the circuits enter a building or structure. Are these disconnects from an outdoor generator required to meet the rules in Article 225? Is there a maximum number of disconnects permitted?
220.14 Other Loads—All Occupancies Article 220 of the National Electrical Code (NEC) contains requirements for calculating branch-circuit, feeder and service loads. Knowing how to perform load calculations is an essential part of being an electrician.
Hidden within the rewrite of Articles 511 and 514—which cover repair garages for motor vehicles and motor fuel dispensing stations, respectively, in the 2005 National Electrical Code (NEC)—is a major change in the concept of hazardous (classified) locations.
An essential part in the life of an electrician is performing load calculations. Determining what size conductors and overcurrent protective devices to install is something most electricians do on a daily basis.
Providing branch-circuit overcurrent protection and subdividing electrical resistance-heating elements in appliances and fixed electric space heating equipment has been a long- standing requirement in the National Electrical Code (NEC).
Electric service for grounding-electrode conductors Q: The electric utility in our area requires the installation of a ground rod and grounding-electrode conductor in the meter socket. Is it acceptable to ground the grounded-circuit conductor (neutral) in the service-disconnect enclosure?
220.1 Scope Understanding how to perform load calculations is an important part of an electrician’s professional career. Before obtaining a permit, some jurisdictions require paperwork showing load calculations for services and feeders.
A new article has been proposed for the 2008 National Electrical Code (NEC) covering mission-critical electrical systems installed in vital infrastructures or facilities where, if the infrastructure or facility was either destroyed or incapacitated, disruption of the facility would affect national
AC and MC bushings Q: Sections 320.17 and 330.17 indicate that Types AC and MC cables must be installed in accordance with 300.4, which includes protection of the cables by listed bushings or listed grommets that cover all metal edges of metal studs.
314.28 Pull and Junction Boxes Requirements pertaining to the installation and use of all boxes and conduit bodies used as outlet, device, junction or pull boxes are in Article 314 of the National Electrical Code (NEC).
Recent discussions on ground-fault circuit interrupter (GFCI) protection for personnel on construction sites have indicated that there seems to be a misunderstanding of whether generator power is excluded from the GFCI requirement.
Outside feeder grounding and bonding Q: What grounding and bonding requirements apply to an outside feeder that supplies a woodworking hobby shop that is located in a detached building and is about 60 feet from, and supplied from, a single-family residence?
314.28 Pull and Junction Boxes Chapter 3 of the National Electrical Code (NEC) covers wiring methods and materials. Article 314 covers the installation and use of all boxes and conduit bodies used as outlet, device, junction or pull boxes, depending on their use.
Within the past few years, many of us have installed surround sound systems in homes and business. What seems to be lacking is an understanding of the new requirements that have been incorporated into the totally revised Article 640 in the National Electrical Code (NEC).
Many professional contractors called to provide a fire alarm system in either a new or existing building have heard the owner exclaim, “I just want to meet code!” Most building owners (especially those not knowledgeable in the code process) have made the assumption that if they instruct you to “jus
Q: Should 250.34 or Article 702 apply to a portable generator that is connected to a domestic refrigerator, freezer, television set, and floor and table lamps in a one-family residence? A: The answer depends on the method used to connect the generator to the appliances.