210.70 Lighting Outlets Required The National Electrical Code states its purpose as “the practical safeguarding of persons and property from hazards arising from the use of electricity.” [90.1(A)] The adequacy of the Code is covered in 90.1(B).
210.70 Lighting Outlets Required Article 210 specifies provisions for all branch circuits except for branch circuits supplying only motor loads. Article 430 contains motor load requirements. Provisions stipulating the placement of receptacle outlets are covered in 210.52 through 210.63.
CODE CITATIONS Article 210 Branch Circuits Article 220 Branch Circuit, Feeder and Service Calculations Article 250 Grounding Article 334 Nonmetallic Sheathed Cable: Types NM, NMC, and NMS Article 422 Appliances The General Information for Electrical Equipment Directory published by Underwriters Labo
210.63 Heating, Air-Conditioning and Refrigeration Equipment Outlet Article 210 specifies provisions for all branch circuits except for branch circuits supplying only motor loads, which are covered in Article 430.
210.52(H) Hallways Article 210 covers branch circuits except for those supplying only motor loads. Motor-load requirements are covered in Article 430. Receptacle-placement provisions are stipulated in 210.52(A) through (H).
* For reference figures, please refer to ELECTRICAL CONTRACTOR magazine. 210.52(D) Bathrooms Requirements pertaining to receptacle placement inside and outside dwellings are covered in 210.52(A) through (H).
CODE CITATIONS Article 100 Definitions Article 210 Branch Circuits Article 230 Services Article 250 Grounding Article 312 Cabinets, Cutout Boxes and Meter Socket Enclosures Article 445 Generators Article 518 Places of Assembly Disconnect for multiwire branch circuit Q: There was a requirement in the
210.52(C)(5) Receptacle Outlet Location Provisions stipulating the placement of receptacle outlets are covered in 210.52 through 210.63. Requirements for placing receptacles in dwelling units are located in 210.52(A) through (H).
210.52(C)(3) Peninsular Counter Spaces Article 210 covers branch circuits except those that supply only motor loads. Motor load requirements are covered in Article 430. Receptacle placement provisions for dwelling units are stipulated in 210.52(A) through (H).
CODE CITATIONS Article 90 Introduction Article 110 Requirements for Electrical Installations Article 250 Grounding Article 404 Switches Article 430 Motors, Motor Circuits and Controllers Article 440 Air Conditioning and Refrigerating Equipment Routing grounding electrode conductor Q: We have to inst
Since the 1980s, the National Fire Protection Association’s fire alarm standards have required the notification appliance (speaker) circuits used in high-rise building Emergency Voice/Alarm Communications systems to “survive” during a fire.
CODE CITATIONS Article 110 Requirements for Electrical Installations Article 230 Services Article 240 Overcurrent Protection Article 310 Conductors for General Wiring Article 430 Motors, Motor Circuits, and Controllers Article 450 Transformers and Transformer Vaults Article 695 Fire Pumps Warning si