Cooking Equipment Calculations, Part III 220.19 Electric Ranges and Other Cooking Appliances Article 220 of the National Electrical Code contains specifications for calculating branch-circuit, feeder and service loads.
Specifications for calculating branch-circuit, feeder and service loads are in Article 220 of the National Electrical Code. This article is divided into four parts: I. General, II. Feeders and Services, III. Optional Calculations for Computing Feeder and Service Loads and IV.
Article 220 contains provisions for calculating branch-circuit, feeder and service loads. Following the requirements set forth in this article will provide the minimum size branch circuit, feeder or service.
CODE CITATIONS Article 210 Branch Circuits Article 250 Grounding Article 408 Switchboards and Panelboards Article 430 Motors, Motor Circuits and Controllers Article 680 Swimming Pools, Fountains and Similar Installations Volume One of the 2003 edition of the Fire Resistance Directory published by Un
Article 210 specifies provisions for all branch circuits except for branch circuits supplying only motor loads. Article 430 contains motor load requirements. Branch circuits with combination loads (motor and non-motor) must be installed in accordance with Articles 210 and 430.
This is the conclusion of a two-part article that began in the November issue. This part provides important information for listing and National Electrical Code requirements for installations of emergency, legally required standby and optional standby systems.
210.70(A)(2) Lighting Outlets Required Lighting outlet and wall switch provisions for dwelling units, guest rooms (hotel, motel and similar occupancies) and certain areas in non-dwelling occupancies are covered in 210.70(A) through (C).
Though lightning season may be over by now, it is worth reviewing the impact storms can have on the operation of a facility. Some may have experienced significant damage to equipment from the high frequency transient energy of lightning strikes.
210.70(A)(2) Lighting Outlets Required Branch circuit requirements are covered in Article 210 of the National Electrical Code. Part III of Article 210 covers required receptacle outlets and lighting outlets.
210.70(A)(2) Lighting Outlets Required Requirements specifying wall switch-controlled lighting outlets (or receptacles) are covered in 210.70. This section contains three subsections: dwelling units, guest rooms and other than dwelling units.
The new type of GFCI employing the latest technology comes with a caveat that must be brought to our attention. Do not get the impression that if this type of receptacle is wired incorrectly that a person cannot be killed or injured.
210.70(A)(1) Lighting Outlets Required Lighting outlet requirements are covered in the last section of Article 210. Branch circuits supplying lighting outlets must be installed in accordance with the provisions in 210.70(A) through (C).