Article 210 specifies provisions for all branch circuits except for branch circuits supplying only motor loads. Article 430 contains motor load requirements. Branch circuits with combination loads (motor and non-motor) must be installed in accordance with Articles 210 and 430.
Jim Dollard has an extensive background in codes and standards. If you have a query about the National Electrical Code (NEC), Jim will help you solve it. Questions can be sent to email@example.com. Answers are based on the 2014 NEC. Grounding electrode conductor termination