Box Fill Calculations, Part I, appearing in June’s issue, introduced box fill, with emphasis on Section 370-16(a). Notably, Table 370-16(a) is used to determine the maximum number of conductors (for sizes No. 18 through No. 6) permitted within common-size metal boxes.
If you have a problem related to the National Electrical Code (NEC), are experiencing difficulty in understanding a Code requirement, or are wondering why or if such a requirement exists, ask Charlie, and he will let the Code decide. Questions can be sent to email@example.com.