Q: Does the National Electrical Code permit Class 2, Class 3 and telephone conductors to be installed in the same bored hole in a wooden stud with Type NM or Type AC cable operating at 120V?
Jim Dollard has an extensive background in codes and standards. If you have a query about the National Electrical Code (NEC), Jim will help you solve it. Questions can be sent to firstname.lastname@example.org. Answers are based on the 2014 NEC. Grounding electrode conductor termination