The required placement of receptacles in the wall above a kitchen countertop is uncertain where an appliance garage is present. The Code requirements are the following: “210.52 Dwelling Unit Receptacle Outlets. (C) Countertops (1) Wall Counter Spaces.
transformer secondary conductor rules are similar to tap conductor rules. Article 240.21 of the National Electrical Code (NEC) covers the location and sizing requirements of overcurrent protection for tap conductors and transformer secondary conductors.