Someone recently asked me to explain the differences between the 10-foot tap rule and the 25-foot tap rule as they apply to feeders. An additional question was raised about connecting multiple taps to the same feeder using both the 10- and 25-foot tap rules.
Jim Dollard has an extensive background in codes and standards. If you have a query about the National Electrical Code (NEC), Jim will help you solve it. Questions can be sent to firstname.lastname@example.org. Answers are based on the 2014 NEC. Previous use of gray conductors