Section 240.21 in the National Electrical Code (NEC) contains feeder tap rules. As defined in 240.2, a tap conductor has overcurrent protection ahead of its point of supply that exceeds the value permitted for similar conductors that are protected as described elsewhere in 240.4.
Charlie Trout, author of Code FAQs and Code Question of the Day, has retired. For the rest of 2013, enjoy these snippets from his daily responses. Calculating conductors and breakers